Generator Installations were asked to supply and install a 2500 litre double skinned fuel tank for a large retail distribution centre in Milton Keynes. The tank was delivered with intergral fill point, gauges and overfill alarm.
Once the tank was offloaded and positioned, connections had to be made between the tank and the generator containers, this was achieved using a pipe in pipe system with a welded mild steel outer and a flexible inner pipe. The inner pipe operating as the fuel transfer line and the outer pipe used as a bund incase there was a leak with the inner pipework. GI also installed a leak dection alarm to notify the end user of any leaks if they occurred in the future.Share